Now hiring Licensed Plumbers and Apprentices
Imperial Plumbing serves all of the city of Denton, Texas including zip codes 76207, 76201, 76209, 76205.
Water Heater Installation Requirements Info:
Water Heaters installed in attics
Attics containing a water heater shall be provided with an opening and unobstructed passageway large enough to allow removal of the water heater. The passageway shall not be less than 30 inches (762 mm) high and 22 inches (559 mm) wide and not more than 20 feet (6096 mm) in length when measured along the centerline of the passageway from the opening to the water heater. The passageway shall have continuous solid flooring not less than 24 inches (610 mm) wide. A level service space at least 30 inches (762 mm) deep and 30 inches (762 mm) wide shall be present at the front or service side of the water heater. The clear access opening dimensions shall be a minimum of 20 inches by 30 inches (508 mm by 762 mm), or larger where such dimensions are not large enough to allow remooval of the water heater.
Water Heaters above ground or floor
When the attic, roof, mezzanine or platform in which a water heater is installed is more than eight (8) feet (2438 mm) above the ground or floor level, it shall be made accessible by a stairway or permanent ladder fastened to the building.
Exception: A max 10 gallon water heater (or larger with approval) is capable of being accessed through a lay-in ceiling and a water heater is installed is not more than ten (10) feet (3048 mm) above the ground or floor level and may be reached with a portable ladder.
Whenever the mezzanine or platform is not adequately lighted or access to a receptacle outlet is not obtainable from the main level, lighting and a receptacle outlet shall be provided in accordance with Section 502.1.
Denton Plumbing Code Tips:
Requirements for discharge piping
The discharge piping serving a pressure relief valve, temperature relief valve or combination thereof shall:
Serve a single relief device and shall not connect to piping serving any other relief device or equipment.
Exception: Multiple relief devices may be installed to a single T & P discharge piping system when approved by the administrative authority and permitted by the manufactures installation instructions and installed according to those instructions.
Location of shutoff valves
Shutoff valves shall be installed in the following locations:
Outstanding reps for the overall warranty process.
Fast and friendly service. Had 2 problems and they were resolved quickly.
Toby with Imperial Plumbing did a fantastic job. Service was prompt; he came out the day after the initial phone call. Toby was both efficient and effective. He answered all of my questions (I had a lot because I'm a new homebuyer) and walked me through some tips. I would absolutely hire Imperial Plumbing in the future if the need arrises.
Toby and Jeremy were terrific. Showed up when they said they would, did what they said they would do and then some. They know their stuff. Great guys.
Toby was very helpful in directing us to obtain the parts necessary for repairs, then promptly making the repairs.
Very satisfied with the service Difficult problem with bath room faucet solved by gooden.
I don't share opinions often when it comes to service so it has to be pretty good in order to get me to take the time to write something. Let me say I am extremely pleased with the service I got from Toby. He was prompt, courteous, knowledgeable and went above and beyond when it came to my service situation. I would recommend him personally and his company Imperial Plumbing wholeheartedly to anyone in this area. My broken water heater and the resultant upgrades to bring me in line with code happened promptly. No hot water makes for a pretty bad day in my opinion. Thanks Toby, you made it much easier!
Prompt and reasonable